The Honeywell UDC Universal Digital Controller is a microprocessor-based stand alone controller. It combines the highest degree of functionality and. Find great deals for Honeywell UDC Universal Digital Controller. Shop with confidence on eBay!. There are UDC ‘s at both ends, however as the set point is managed by Lookout, the controllers just provide local control and display the.
|Published (Last):||7 May 2014|
|PDF File Size:||15.42 Mb|
|ePub File Size:||13.41 Mb|
|Price:||Free* [*Free Regsitration Required]|
It’s free, and you can customize the content you view, as well as being able to subscribe to threads and topics, getting new posts delivered to your email as they appear. Inlet Flow and Outlet Flow.
Please log in and try again. Open the gate x amount for x period.
Honeywell UDC 3000 Universal Digital Controller
The inlet control is likely configured for reverse operation increaed level decrease output, close gate. You have given some good problem definition.
First mention your complete model no. Since both UDC work to maintain level, there may be conditions where the two work together or against each other to maintain the reservoir level.
Username Password Remember me on this computer. So that i can help you to resolve the problem.
Note that common words and, that, etc. NandaKumar on 16 July, – 8: Since the two can be connected through Lookout, you may consider implementing a staged control wherein the downstream UDC handles a majority of level changes in the reservoir small deviations in level.
The bound manual you are looking for is Product E. Thanks for the reply. I would like a little more clarification on what your measuring and what your controlling – ‘gate position’ is pretty hard to measure unless you have some sort of valve 33000 arrangement.
You have clicked on the “? Your subscription request is being processed.
Honeywell UDC – In Stock, We Buy Sell Repair, Price Quote
By Anonymous on 23 July, – To exclude a word, precede it with a “-“, as follows: Some tips for better search results Select the categories for which you would like to see messages displayed The lake receives water from a river and releases it to the same down stream. Welcome to the Modbus Community, about the world’s leading automation protocol.
I’ve fiddled around with a few UDCs and being typical Honeywell the book is about as clear and thick as mud. To search the site, enter your search terms in the box labeled “search the site” and hit Enter. Try those and reply if its still not working. The ‘Rng1’ error your getting refers to the analogue input UDC’s are twin-loop controllers though in your application loop 2 is disabled It shows that error when the input range goes above 20ma or below 4ma.
This control occurs at two places on the reservoir: By Patti on 4 November, – 2: Use double quotes around phrases, as follows: By Steve Smoker on 4 October, – 7: Adjust the head gate position to maintain reservoir level. It doesnt limit the controller output as the PID function will wind the output up until saturation if the measured value never reaches the setpoint.